Remote boiler control with Ferroli ROMEO W/RF OpenTherm thermostat and Marmitek UM7206 X10 module
We turn our heating off when we are away, so when we came back, the flat was at a balmy 7 degrees centigrade. Needless to say, it took a number of days to heat it back up to reasonable temperature.
Since we already have a Ferroli boiler connected to a ROMEO W/RF (P/N: 013101XA) wireless OpenTherm thermostat, I've decided to try set it up to enable us to switch the heating on remotely.
I always wondered what those "GSM" terminals on the RF bridge were for. In the thermostat manual, I noticed the following at the bottom of the last page :
If the telephone contact (voltage-free contact) has to be connected, use the "GSM" terminals
I asked Ferroli UK support to clarify the operation of these contacts, but they didn't know and referred me to the factory in Italy. At the time of writing, the factory has not come back to me.
I did however stumble upon a hint on one of the forums on how to make this work, so if you have one of these thermostats and would like to set it up for remote control away from home, read on..
- ROMEO W/RF (013101XA) OpenTherm thermostat, already connected, configured and working[n1]
- Marmitek UM7206 X10 low-voltage relay module
- X10 stack of your choice, already configured and working or USB relay[n2]
This guide assumes you have a working X10 stack already.
By default, the thermostat is configured to switch the boiler OFF when the "GSM" contacts on the ROMEO W/RF wireless bridge PCB are connected together and resume normal (daily/weekly programmed) operation when the contacts are disconnected.
This guide assumes you are looking to switch your boiler ON instead, when the GSM contacts are connected together.
You'll need to change the following registers, by pressing and holding down the "P" button (button #7 in the diagram from the manual) and then keep pressing it until you get to P8 register. The following table from the manual lists the defaults for P8 and P9 registers:
Set P8 to 1 (1=Switch ON heating when GSM contacts are connected together) and also set P9 to desired temperature in this mode (e.g. 21.5C). This is the temperature the thermostat will try to maintain, while it is in the remote operation mode.
Marmitek UM7206 Setup
Set the unit and house codes on the device using the two dials to match your X10 configuration. Set the slider on the left to "continuous" and the slider on the right to "relay only" (unless you want a bit of noise pollution).
Now, push the manual ON switch on your UM7206 unit. Observe the RF remote control panel, it should show the boiler entering "manual heating mode" (icons #15, 21 and 19) as well as an undocumented flashing icon "()", which should appear below #23:
Note, it may take up to 120 seconds for the boiler/thermostat to respond as the "GSM" contacts are changed, so please be patient.
The boiler will work in this mode and maintain a constant temperature, set using register P9. Also, in this mode, the ROMEO remote control panel will not allow the temperature to be changed, until such time, that the GSM contacts are disconnected (i.e. you push the OFF button on the UM7206).
That is about it. The UM7206 relay can be controlled using X10 commands from your X10 controller and if you have allowed access to it from the Internet, you can switch your boiler on remotely a day or so before you are due back from your holiday. That way you arrive at a warm house, instead of having to sit in your woollen hat and gloves nursing a cup of hot tea, while waiting for your dwelling to return to the habitable zone.
When you do arrive back, don't forget to switch the boiler back into programmable mode by either pushing the OFF button on the Marmitek UM7206 or by issuing the appropriate X10 command via your interface.
I choose to use X10 interface because I already have it up and running. If you don't want to use the X10 interface, there are a number of other ways to implement this remote switching capability.
All you really need is a relay you can control with a computer, which is going to close/open the GSM contacts on the ROMEO wireless RF bridge. You can use a single channel USB relay module, plugged into a computer of your choice (e.g. Raspberry Pi) and as long as you can connect to your computer remotely, you can issue a command to control the connected relay from anywhere.
However, regardless of the control implementation you choose, I would recommend to secure your control system using either a VPN and/or SSL with strong password.
[n1] For some reason ROMEO W/RF is not available in the UK, but you can order it direct from eBay.it or from vendors in Italy/Poland/Russia.
[n2] I use CM12U connected to Raspberry Pi running HEYU with domus.Link front-end.
[n3] Ferroli ROMEO W/RF manual (EN)